A New Method for Quick and Easy Synchronization of CHP Resources with an EPS
(*) Corresponding author
the author of the article can submit here a request for assignment of a DOI number to this resource!
Cost of the service: euros 10,00 (for a DOI)
This article provides new ideas for synchronization between an electrical power system (EPS) and a combine heat and power (CHP) system. If an AC generator is used with another AC system, synchronization turns to an indispensable process. It is a frequent event for combined heat and power cogeneration in small quantities and is one of the most important things in daily operation. Also closing the breaker at zero phase difference is very important in synchronization. In this paper we introduce new ideas which will lead two AC systems to a smooth and soft synchronization. Through these ideas a soft synchronization which can provide a perfect phase angle matching is realized. In order to verify the efficiency of the proposed synchronization, matlab program was used for simulation studies and experimental tests were done through using with a real synchronous generator.
Copyright © 2013 Praise Worthy Prize - All rights reserved.
P.Piagi ahd R.H.Lasseter, “Microgrids:A conceptual solution,” Power Electronics specialists Conference, vol.6,pp. 4285-4290, 2004.
P.Piagi and H.R.Lasseter, “ Autonomous control of microgrid,” power Engineering Society General Meeting, 2006, Dol 10.1109/EPS.2006.1708993.
CERTS, “Integration of distributed energy resources – The CERTS microgrid concept” Submitted to the U.S Department of Energy April 2002.
R.H.Lasseter, “Microgrid” Power Engineering Society Winter Meeting,vol. 1,pp. 164 – 169, 2001.European Conference on Power Electronics and Application , pp P.1-P.10.
Bell,M. ,M.Swinton, E.Entchev, J.Gusdorf, W.Kalbfleisch, R.Marchand,and F.Szadkowsk,2004. “Testing Residential Combined Heat and Power Systems at the Canadian Center for Housing Technology.” In proceedings of the ACEEE council for an energy efficient economy.
Mashhour, M., Golkar, M.A., Moghaddas Tafreshi, S.M., Aggregated model of distribution network with distributed resources, (2009) International Review of Electrical Engineering (IREE), 4 (4), pp. 583-591.
W.M.Strang, C.J.Mozina, B.Beckwith, T.R.Beckwith, S.Chhak, E.C.Fennell, E.W.Kalkstein,K.C.Konzminski, A.C.Pierce, P.W.Powell,D.W.Smaha,J.T.Uchiyama, S.M.Usman, and W.P.Waudby, “Generator synchronizing , industry survey results” IEEE Trans.Power Del.,vol. 11,no.1,pp.174 – 183, Jan.1996.
L.C.Gross, L.S.Anderson, and R.C.Young , “Avoid generator and system damage due to a slow synchriniaing breaker,” In Proc.25th Anuu.Western Protective Relay Conf., Oct. 21 - 23 , 1997,pp. 1 – 20.
J.V.Mitsche and P.A.Rusche, “Shaft torsional stress due to asynchronous faulty synchronization,” IEEE Trans. Power App.Syst.,vol.PAS-99, no.5,pp. 1864-1870, Sep.1980.
R.A.Evans and P.E.,”A manual/automatic synchronization circuit for a 37.5 MVAsteam turbin driven generator,” IEEE Trans.Ind.Appl.,vol.26,no.6,pp.1081-1085,Nov/Dec.1990.
V.Kaura and V.Blasko, ‘Operation of a phase locked loop system under distorted utility conditions,’ IEEE Trans. Ind.Applicat., vol.33,pp.58-63,Jan.1997.
M.M.Begovic, P.M.Djuric, S.Dunlap, and A.G.Phadke, “Frequency tracking in power networks in the presence of harmonics,” IEEE Trans.Power Del.,vol.8,no.2pp.480-486,Apr.1993.
K. Koellner, C. Anderson, and R. Moxley, “Generator black start validationusing synchronized phasomeasurement,” in Proc. IEEE PowerEn. Soc. Power System Conf. Expo., Oct. 2006, pp. 1356–1362.
H.-S. Song and K. Nam, “Instantaneous phase-angle estimation algorithmunder unbalanced voltage-sag conditions,” in Proc. Inst. Elect.Eng. Generation, Transmission, and Distribution, vol. 147, 2000, pp.409–415.
 F. M. Gardner "Phase Lock techniques", New York: Wiley, 1979.
MATLAB, SimPowerSystems reference.(R2012a). [Online].Available:http://www.mathworks.com/products/simpower/
Q. Zeng and L. Chang, “A new method for three-phase voltage detectionand protection based on reference frame transformation,” inProc. IEEE Power Electronics Specialists Conf., Aachen, Germany,Jun. 21–24, 2004, vol. 4, pp. 2489–2493.
P. Rodriguez, L. Sainz and J. Bergas "Synchronous Double ReferenceFrame PLL applied to a Unified Power Quality Conditioner", Harmonicsand Quality of Power, 2002. 10th International Conference on Volume2, 2002 pp:614 - 619.
Woodward, Installation & Operation Manual for SPM-a Synchronizer.[Online].Available:https://www.woodward.com/pubs/download.cfm?link=/PDF/IC/82384.PDF
J. Svensson, “Synchronization methods for grid-connected voltagesource converters,” in Proc. Inst. Elect. Eng. Generation, Transmission,Distribution, vol. 148, May 2001, pp. 229–235.
K. E. Yeager and J. R. Willis, “Modeling of emergency diesel generatorsin an 800 megawatt nuclear power plant,” IEEE Trans. EnergyConvers., vol. 8, no. 3, pp. 433–439, Sep. 1993.
Wang, Y., Wang, Y., Modal analysis of stator system of large turbo-generator, (2013) International Review of Electrical Engineering (IREE), 8 (2), pp. 681-689.
- There are currently no refbacks.
Please send any question about this web site to firstname.lastname@example.org
Copyright © 2005-2023 Praise Worthy Prize